The product is a new energy-saving switch, It adopts integrated circuits and a good sensitivity detector. It incorporates automatism, convenience, energy-saving way, and practicality. It works by receiving human motion infrared rays. It can start the controlled load at once when one enters the detection field. It can identify day and night automatically. Its installation is very convenient and wide using range. It has the functions of power indication and detection indication.
Can Identify day and night. The consumer can adjust work ambient light. Int can work in the daytime and at night when it is adjusted on the “sun” position(max). It can work in the ambient light of less than 3LUX when it is adjusted on the “moon” position(min). As for the adjustment pattern, please refer to the testing pattern.
Time-Delay is added continually. When it receives the second induction signals after inductions, it will compute time once more on the basis of the first time-delay rest.
Time-Delay is adjustable. It can be set according to the consumer’s desire. The minimum time is 10sec±3sec. The maximum is 8min±2min.
Switch off the power.
Turn clockwise to the bottom-stand and take off it. The power wire crosses the hole in the middle bottom-stand. The bottom-stand is fixed on the selected position with an inflated screw.
Connect the power and the load into the connection-wire column of the sensor.
The sensor aimed at the mouth of the bottom-stand and turned anti-clockwise.
Turn the TIME knob to the minimum (-) position with an anti-clockwise. Turn the LUX knob to Sun position anti-clockwise.
Switch on the power, the collected load, and the indication lamp both are not working. Preheat 30 seconds later, the load and indication lamp should be turned on synchronization. In the absence of no inductor, the lamp is turned off. Working within 5-30sec, the inductor lamp is turned off.
After the first sense is finished, and it will sense again after 5~10sec. The load should work. When there are no inductor signals in the inductor lamp, the load should be stopped working within 5-15sec.
Turn the LUX knob clockwise on the minimum (MOON Position). If it is adjusted in less than 3LUX, the inductor load should not work after the load stops working. If you cover the detection window with the opaque(towel etc), the load works under no induction signal condition, the load should stop working within 5-15sec.
|Power Sourcing||220V-240V AC|
|Detection Range||120°(side view) and 360 (top view)|
|Working Temperature||-10° to 40° C|
|Ambient Light||<3 LUX (Adjustable)|
|Time-Delay||min. 10sec±2sec and Max. 7mint±2min|
|Power Consumption||0.5W (work) and 0.1W (static)|
|Rated Load||1200W Max. Tungsten and 300W Max. Fluorescent|
|Detection Motion Speed||0.6-1.5m/s|
|Detection Distance||6m max (<24° C)|